From the AS/NZS 3008.1.1:2017, the voltage drop for 4 mm² is 14.3 V/A.km. Because the PV mannequin present at MPP is the same as 8.2 A and the DC cable size from the string to the AJB is meant to be 2 m. Thus, the voltage drop from the PV string to AJB (Vdrop, string to AJB) is the same as 0.235 V in each arrays.
As given on this instance that the every day location irradiation on tilted floor is the same as 5.93 kW/m². Thus, the typical photo voltaic radiation () is 494.17 W/m².
Because the minimal ambient temperature and most ambient temperature on this website are equal to -5 °C and 40 °C, respectively. As well as, the NOCT is the same as 46 °C. Then, to search out the minimal and most cell temperatures, could be obtained as follows: